Chapter 27 UTILITIES*
Section 27-99 Current transformers.
(a) When, in the judgment of the director, the maximum load
on a service will exceed two
hundred (200) amperes, such service shall be metered by the use of current transformers. The
department will furnish the current transformers, and if installed outdoors, the department will
install the current transformers. The customer shall provide a suitable mounting space for the
current transformers at the supply end of the service entrance.
(b) If mutually agreed by the customer and the department,
the current transformer may be
installed indoors. If installed indoors, the customer shall furnish and install an approved
enclosure and shall install the department's current transformers in the enclosure. When current
transformers are used, the customer shall furnish all material required for the meter loop in
accordance with all other applicable provisions of these ordinances.
(Code 1964, § 15.452)